edwards eh500 manual
File Name:edwards eh500 manual.pdf
Size: 4832 KB
Type: PDF, ePub, eBook
Uploaded: 11 May 2019, 23:33 PM
Rating: 4.6/5 from 777 votes.
Last checked: 2 Minutes ago!
In order to read or download edwards eh500 manual ebook, you need to create a FREE account.
eBook includes PDF, ePub and Kindle version
edwards eh500 manualPTB Sales' expert team of engineers can configure products to your specific needs. Please follow the above link, and fill out the quote form. Learn More Like all blowers, it requires a suitable backing pump such as an Edwards E2M40 and E2M80. Download the full manual below. As with all mechanical devices, regular maintenance can help ensure optimised, safe performance of your Edwards EH Series mechanical booster pump. Oil Condition The condition of oil used in mechanical booster pumps deteriorates over time and by contamination from process gases and byproducts, indicated by a progressive change of oil colour. Regular replacement of oil will minimise wear and tear on contacting parts and prolong good vacuum performance. Edwards recommends checks on the oil either daily if the materials being pumped are flammable or weekly for nonflammable materials. Recommendations for replacing the oil and lubricating rear bearing on a yearly basis. Act responsibly and safely Edwards cares about the health and safety of people and the environment. Please remember to dispose of used or contaminated oil, cleaning solutions and components responsibly and safely. Discontinue operation, overhaul pump and change oil Edwards services If you prefer maintenance of your products to be performed with the assurances and guarantees of OEM standards, Edwards offers a full range of maintenance, overhaul and exchange services that include safe disposal of oil, fluids and used components. Contact us for further information. Prices are indicative only and may vary by country, with changes to the cost of raw materials and exchange rates. Electrical Apparatus for Potentially Explosive Atmospheres. Part 1: General Requirements. Part 5: Flameproof Enclosure 'd'. Machinery Safety Directive. Electromagnetic Compatibility Directive. Low Voltage Directive. Electrical Apparatus for Use in Potentially Explosive Atmospheres Directive.http://xo-sound.ru/userfiles/d-link-extender-manual.xml
- edwards eh500 manual, edwards eh500 manual, edwards eh500 manual, edwards eh500 manual pdf, edwards eh500 manuals, edwards eh500 manual user, edwards eh500 manuale, edwards eh500 manual guide, edwards eh500 manual instructions, edwards eh500 manual typewriter, edwards eh500 manual transfer switch, edwards eh500 manual.
Only applicable to the flameproof motors on EH1 200c, EH2600c and EH4200c pumps. All of thepumps are abbreviated to EH pumps in the remainder of this manual. You must use your EHpump as specified in this manual.Read thismanual before you install and operate your EHpump. Important safety information ishighlighted as WARNING and CAUTION instructions; you must obey these instructions. Theuse of WARNINGS and CAUTIONS is defined below. WARNINGWarnings are given where failure to observe the instruction could result in injury or death to people. CAUTIONCautions are given where failure to observe the instruction could result in damage to the equipment, associated equipment and process. The units used throughout this manual conform to the SI international system of units ofmeasurement. 1.2 DescriptionThe EH pumps are compact and have high pumping speeds. Youmust use the EH pumpwith asuitable backing pump. The EH pumps can operate with amaximum continuous inlet pressureof 1000 mbar. You can achieve low system pressures by the use of two or more EH pumps inseries.The EH pump coupling-cover is connected to the pump outlet and forms an integral part of thevacuum system. The connecting lines have a filter which removes debris and so preventscontamination of the lubricating oil and bearings. For an even cleaner system, you can evacuatethe coupling-cover and bearings by connection to the pump-inlet or to an external vacuumpump.The hydrocarbon safe area and chemical EHpumps use hydrocarbon oils, such asUltragrade 20.Versions of the safe area pumps for usewith PFPE (perfluoropolyether) oils are also available forvacuum systems in which oxygen or other reactive or corrosive gases are pumped.All the EH pumps have ISO inlet-flange and outlet-flange connections. EH Mechanical Booster Pumps 1 1.3 General constructionTheEHpumps arepositive displacement Roots vacuumpumps. Thepumpmechanism isdrivenby a three-phase electric motor through a hydrokinetic fluid-coupling.http://fredgillen.com/userfiles/d-link-dwl-g810-manual.xmlThe EH250, EH500A, EH1200, EH2600 and EH4200 pumps are all fitted with safe area motors.The EH1200C, EH2600C and EH4200C pumps are all fitted with flameproof motors (seeSection 1.4.1). All of the motors are air-cooled.The pump shafts and rotors are made of high-grade, corrosion-resistant, cast-iron. The internaland external shaft-seals are made of polytetrafluoroethylene (PTFE) or fluoroelastomer.Thepump-bearings, gears and seals are lubricatedbyoil fed from reservoirs in the coupling- cover. Aseries of seals stops the oil from reaching the vacuum side of the pump. The coupling- cover isevacuated. You can inspect the oil-levels through sight-glasseswhich are fitted to the coupling-cover.Oil-filler, oil-drainage and external evacuation connections are provided on the cover.The timing gears on the EH1200, EH1200C, EH2600, EH2600C, EH4200 andEH4200Cpumps arelubricated by oil inside the gear-cover. An oil-filler connection is provided and you can inspectthe oil-level through a sight-glass fitted to the gear-cover. 1.4 'C' model chemical EH pumps 1.4.1 Flameproof motorsThe EH1200C, EH2600C and EH4200C chemical pumps are all fitted with flameproof motors: Pumps suitable for 50 Hz operation are fitted with a flameproof motor approved to EEx d, Gas Group IIA, IIB, Temperature Class T4. You can connect a suitable purge gas supply to this connector, to provide for coupling-cover purge with nitrogen at positive pressure. This will purge the shaft-seals, and prevent theentry of corrosive or toxic vapours into the coupling-cover and gear-cover.A fixed restrictor in the connector ensures that the correct amount of nitrogen is allowed to flowinto the coupling-cover. 1.4.3 After-coolerThe EH1200C, EH2600C and EH4200C chemical pumps have an after-cooler in the pump outlet.On the EH2600C and EH4200C pumps, this after-cooler is resistant to corrosive vapours whichmay condense on it during pump operation (depending on the application). 2 EH Mechanical Booster Pumps 1.https://labroclub.ru/blog/boss-br900cd-owners-manual5 Principle of operationThe EH pump is shown in Figures 1 and 2. The motor-shaft drives one of Recommended Coupling between Deformation, Fluid Pressures, and Fluid. Discover everything Scribd has to offer, including books and audiobooks from major publishers. Start Free Trial Cancel anytime. Report this Document Download Now Save Save Booster Manual Condensed For Later 0 ratings 0 found this document useful (0 votes) 14 views 15 pages Booster Manual Condensed Uploaded by Jonathan Velasquez Castro Description: manual de bomba de vacio Booster Full description Save Save Booster Manual Condensed For Later 0 0 found this document useful, Mark this document as useful 0 0 found this document not useful, Mark this document as not useful Embed Share Print Download Now Jump to Page You are on page 1 of 15 Search inside document Browse Books Site Directory Site Language: English Change Language English Change Language. Page Count: 58 Page i Edwards and th e Edwards logo are tradem arks of Ed wards Limited.Page iii Edwards and th e Edwards logo are tradem arks of Ed wards Limited.All ri ghts re served. Edwards and the Edward s logo a re trademarks of Edwards Limited. Page 1 Edwards and th e Edwards logo are tradem arks of Ed wards Limited. Introduction A705-61-88 0 Issue K 1I n t r o d u c t i o n 1.1 Scope and definitions This manual pro vides insta llation, operat ion and ma intena nce instructions for the Ed wards GV Dry Vacuum Pumps (abbreviated to GV pump(s) or pump(s) in the remaind er of this manual). You must use the GV pumps as specified in this manual. Read this man ual before y ou install an d operate you r pump. Imp ortant safety informatio n is highlighted as WARNING and CAUTION instructions; you must obey these instructio ns. The use of WARNINGS and CAUTIONS is defined be low. CAUTION Cautions are given where failure to ob se rve the instruction could result in damage to the equi pment, associated equipment and process.http://cqitracker.com/images/cas-weighing-scale-manual.pdf The following IEC warning la bels appear on the pump: The units used throughout this manual conform to th e SI intern ational syst em of units of measurement. Whe re appropriate, US equivalent units of me asurement are also given. 1.2 The GV pumps Refer to Figure 1. The GV pumps are rugged, reliable dry vac uum pumps desi gned fo r general vacuum use. The pump is a three-stage, positive disp lacement rotary pump in which pairs of interm eshing rotors (mounted on common shafts ) are held in correct phase relation by a pair of timi ng-gears. The timing-gears and the adjacent double-row angular contact ball bearings are oil lubricated. The pump has lifti ng-bolts (5) and is mounted on a ro bust fr ame (9). Fixing holes (8) in the frame can be used to secure the pump frame in i ts operating p osition. WARNING Warnings are given where failure to observe the instruction could result in injury or deat h to people. Warning - refer to accompanying documentation. Warning - risk of electric shock. Warning - hot surfaces. Introduction Figure 1 - The GV pump 1. Gearbox 2. Cooling-water outlet 3. T emperature mea suremen t point 4. Thermal snap-sw itch box 5. Lifting-bolt 6. Pump-inlet 7. Cooling-wat er inlet 8. Fixing-holes 9. Frame 10. Gas-ballast flow v alve 11. Exhaust-purge po rt (blanked) 12. Interstag e relief v alve 13. Pump-outle t 14. Oil-level sight-glass 15. Coupling cover 16. Pump-motor 17. Arrow showing mo to r rotation direction 18. Corr ect direction of rotation arrow 19. Motor cooling-fan 20. Oil drain-plug 21. Oil filler-plug 22. Shaft-seals pur ge inlet Page 3 Edwards and th e Edwards logo are tradem arks of Ed wards Limited. Introduction A705-61-88 0 Issue K 1.3 Gas system Refer to Figure 1. The pump has a shaft-seals p urge system and a gas -ballast system. You can connect a dry comp ressed air sup ply to the shaft-se als purge inlet (22). The sh aft-seal s purge pipeline then delivers the dry air purge t o the shaft-s eals. This dr y air purge: ens ures that th e shaft-seals are maintai ned at a positive pressure during pump operation; prevents the en try of corrosive or toxic proc ess vapours into the pump gearbox; prevents contamination of the process gases by p ump oil; prev ents damage to the sha ft-seals b y debris. As supplied, the gas -ballast system can deliver ambient air to the pump gas-ballast inlet. The air-flow is filtered and is controlled by a valve (10). A check -valve ( Figure 7, item 10) prevents the escape of process ga ses out of the gas- ballast system into the local atmo sphere. The pump-motor (16) is air-cooled by an integral c ooling-fan (19). A thermal snap-switch box (4) is fitted to the pump-body. The snap-switch box has two thermal snap-switche s: z The output of the wa rning thermal snap-switch will go open circuit whe n the temperature of the pump-body is higher than normal. Use this output to provide a warnin g of high pump temperature.Use th is output to shut-down the pump when it is too hot. 1.5 Interstage relief valve The pump has an interstage relief valve (12) fitted in a pi pe between the pump-outlet and the last st age of the pump. The valve is normally held closed by its own weight, bu t opens depen ding on the pump-inlet pressure, as follow s: z At pump-inlet pressures of 30 0 mbar (3 x 10 4 P a, 225 T orr) and above on the GV250, and at pump -inlet pressures of 200 mba r (2.0 x 10 4 P a, 150 T orr) and above on the GV400, the interstage pres sure forces the valve open. This allows process gases to p ass directly from the se cond stage i nto the pump-o utlet, withou t compression in the third sta ge of the pump.P rocess gases pa ss through all stages of the pu mp; that is, the process gases are compre ssed in the third stage before t hey pass into the pump-outlet. The interstage relief valve allows the pump to provide a constant pump ing spee d from atmo sp heric pressure down t o 1 0 m b a r ( 1 x 1 0 3 Pa, 7.5 Torr) and also prevents excessive electr ical po wer consum ption by t he pump-m otor when the pump starts. 1.6 Drive oper ation The pump has a f lexible drive co upling which tr ansmits the drive from the p ump-motor (16) t o the pump rotors. Refer to Figure 12. A coupling hub (14) is fitted to the pump shaf t (9) and a drive hub (16) is fitted to the motor shaft (18). A coupling insert (15) fits between the coupling and drive hubs. Introduction The drive hub incorp orates a number of drille d holes. With a coupling cover (12) removed, you can fit a s teel rod (or other suitable tool) to one of these h o les, and you can then manually turn the drive shaft, and so turn the pump. This facility is useful if, for example, you need to drai n fluid from the pump following a hydrau lic lock (see Table 16 ). 1.7 Liquid pumping capability The GV pump ca n survive the in gress of some liquid (after a process failure condition, for example) withou t damage, however the pump is not suitable for continuous pu mping of liquids. If you want to continuously pump a liq uid stream, contact your supplier or Ed wards for advice. 1.8 Safe area oper ation You must not use the GV pump in the following hazardous are as: z Zone 0, Zone 1 or Zo ne 2 (gases), or Zone Z (10) or Zo ne Y (11) (dusts), as classifi ed by Euro pean authoritie s. z Division 1 or Division 2 (gases a nd dusts), as classified by North American authorities. These hazardous areas requi re the use of flameproof equi pmen t. If you need a pump which can operate in these areas, con tact you r supplie r or Edwards for advice. 1.9 Accessories A number of accessories are av ailab le for the GV pumps; use these to conf igure the pump for specific applicati ons. These accessories are listed in Section 7.4. Page 5 Edwards and th e Edwards logo are tradem arks of Ed wards Limited.Page 7 Edwards and th e Edwards logo are tradem arks of Ed wards Limited.Technical data 2.5 Cooling system 2.6 Lubrication data Note: Edwards Material Safety Data Sheets for the recommended oil and g rease specified in Table 7 are available on request.Page 9 Edwards and th e Edwards logo are tradem arks of Ed wards Limited.Edwards and the Edward s logo a re trademarks of Edwards Limited.Page 11 Edwards and th e Edwards logo are tradem arks of Ed wards Limited. Installation A705-61-88 0 Issue K 3 Installation 3.1 Safety z A suitably trained and supervise d technician must install the pump.Dismantl e and clean con taminate d component s inside a fum e-cupboard.If you do not, you can cause injury to peop le and dama ge to equipment. If you do not, there will be a risk of emission of hazardous gases. WARNING When the pump is switched off, gas will fl ow in reverse direction through the pump and there will be a rapid pressure ri se in the inlet pip eline and your process system. If this will cause a dangerous situation (or if it will adversely affect your proc ess), you mu st incorporate sui table devices (such as a fast-acting inlet isolati on- valve or an outlet ch eck-val ve) in your s ystem pipelines. Edwards and the Edward s logo a re trademarks of Edwards Limited. Installation When you design your system, take note of the following: z Y ou must be able to isolate the pump from the a tmosphe re and from your process system if you have pumped or produc ed danger ous chemica ls z On very dusty applications, incorporate an inlet filte r in the inlet pipeline, to minimise the in gress of dust into the pump z T o get the best pumping speed, ensure that the pipeline which connects the process system to the pump is as short as p ossible and h as an inte rnal diamet er not less than the pum p-inlet.If the pressure in the pipeline is higher than this pressure, th e pump will o perate at a hi gh temperat ure and may t rip because o f excessive electrical current consumption.If necessary, contact Edwards or yo ur supplier for advice on inlet isolation-valves, ou tlet check-v alves or othe r components suitable for your application and system design. 3.3 Unpack and inspect 1. Use a fork-lift truck or a pall et truck to place the pallet in a convenient position. 2. R emov e the cardbo ard sleeve which covers the pump, then remove th e protective foil bag from aro und the pump. 3. Inspect th e equipment. If the pump or any of the other it ems is damaged, notify your suppli er and the carrier in writing wi thin three days; stat e the Item N umber of the pump together with your order number and your supplier ’ s invoice number. R etain all packing materials for inspection. Do not use the pump if it is damaged. 4. Check that you h a ve received the items listed in Ta b l e 1 1. If any of the se items is mi ssing, noti fy your supp lier in writing wi thin three days. 5. If the pump is not to be used i m mediately, replace the packing materials. Store the pump i n suitable conditions as describe d in Section 6.1. WARNING Incorporate safety devices to p revent operatio n of the pu mp when th e exhaust pipeline is restricted or blocked. If you do not, the ex haust pipeline may become over-pressurised and may burs t. WARNING Use suitable lifting equipment to move the pump. If you do not, yo u can injure yourself or damage the pump. Refer to Section 2.3 for the mass of the pump.Page 13 Edwards and th e Edwards logo are tradem arks of Ed wards Limited. Ensure that the cooling-air flow arou nd the pump-motor is not restricted. 1. R efe r to Figure 1. R emove from the fixing-holes (8) the four nuts and bolts which secure the pump frame (9) to the pallet. 2. Attach suitable lifting-eq uipment to the four li fting bolts (5) to move th e pump. 3. Locate the pump on a firm, level surface. Ensure that the surface is clean and free from debris and contamination (such as oil). 4. Use suitable bolts through th e four fixing-holes (8) to se cure the pump in p osition. 3.5 Check the gearbox oil-level Refer to Figure 1. T h e p u m p i s s u p p l i e d f i l l e d w i t h o i l. B e f o r e y o u operate the pump, check that the gea rbox oil-level is correct: the oil-level must be be tween the MIN and MAX mark s on the bezel of th e oil-level sight-gla ss (14): see detail C. If necessary, pour more oil into the gearbox: r efer to Section 5.3. 3.6 Electrical connections 3.6.1 Introduction Note: On 60 Hz pumps, yo u must make the wiring connections in the moto r in accordance with the US National Electrical code and with a pproved local and si te practices We recommend t hat you connect th e electrical supply to the pump -motor through a s uit able current monit or, and that you configure the high current setting on the curren t monitor to switch off the pump-motor at a suitable overload cur rent. This ov erload cur rent must not exceed the maximu m current ra ting shown on the rating pl ate on the pump-motor. Note that the gene ral procedur e to co nnect to the pump-m otor is given in Section 3.6.2. However, you must refer to the motor manual supplied with your pump for deta iled inst ru ctions on how to connect your ele ctrical supply to the pump-motor. WARNING Use suitable lifting equipment to move the pump. Refer to Section 2.3 for the mass of the pump. WARNING Ensure that the electrical insta llation of your pump conforms to your local and national safety requirements. It mu st be suitably co nnected to a fused and protected el ectrical supply and a suitable earth (ground) point. Edwards and the Edward s logo a re trademarks of Edwards Limited. Installation 3.6.2 Connect the electrical supply to the pump-motor Connect the electrical supp ly to the pump-motor as desc ribe d below. You m ust use a su itably sized supply cable. 1. R emov e the cover from the pump-mo tor terminal box. 2. R e move the plug from the cab le entry ho le in the term inal-box ( Figure 1, item 17) 3. Fit a suitable cable-gland and nut to the entry hole, then pass the supply cable through the cable-gla nd. The cable gland that yo u use must be ra ted to provid e seal protection IP55 (in IEC529 or NEMA MG1.pt.5 ). 4. Configure any links in the terminal box as neces sary, then connect the phase conductors and the earth (ground) wire to the terminals in the termin al-box: refer to the motor manual suppl ied with your pump or moto r nameplate. 5. If you will fit separate thermistor s cable c ontinue at Step 6 below, otherwise continue at Step 3 of Section 3.6.3. 6. T ighten the cable-gland nut strain-relie f screws 7. Continue at Section 3.6.3 to connect the thermistor outp uts Page 15 Edwards and th e Edwards logo are tradem arks of Ed wards Limited. Installation A705-61-88 0 Issue K Figure 3 - Schematic diagr am of the recommended electrical connections 1. T o your electrical supply 2. Earth (ground) points 3. Auxiliary contacts (2 off, normally closed) 4. Fuse or circuit br eaker 5. Control voltage 6. Stop control 7. Start control 8. Shut-down thermal snap-switch 9. Inlet-valve control solenoid (optional) 10. Contactor A. Pump-motor connections B. Control circuit Earth (ground) points Location Size Thermal snap-swi tch box M4 tapped hol e Pump-motor - Edwards and the Edward s logo a re trademarks of Edwards Limited. Installation 3.6.3 Connect the thermistor outputs The motor windings are fitted with thermistors, which are termi nated in the motor te rm inal-box. You must connect the thermistor outputs t o a suitable control circuit to is ola te the electr ical supp ly from the p ump-motor an d shut down the pump if the windings overheat. 1. R emov e the plug from one of the cable en tr y holes on the pump-motor ter minal box ( Figure 1, item 17). 2. Fit a suitable cable gland and nut to the entry hole, then pass your control cable through the cable-gla nd. The gland you u se must be ra ted to provid e seal prote cti on of IP55 (in IEC 529 or NE MA MG1.pt.5) or better to the terminal box. 3. Connect the wires in the control cable to the thermistor outpu t terminals in the te rm inal-box: refer to the motor manual supplied wi th your pump or motor nameplate. 4. T ig hten the cable-gl and nut strai n relief scre ws. 5. R efit and secure the terminal box cover. If you do not, you can damage the pump and there may be a risk of fire. WARNING Incorporate a manual reset device in your control equipment. If you do not (and a fault which causes the thermistors to shut down the pump is not corrected ), the pump will automatically switch on agai n when the motor win dings cool down. If you have started mainte nance or fault finding on the pump, there will be a risk of injury to people. 1. Links 2. T erminal-box 3. Earth (ground) terminal 4. Electrical supply cable Page 17 Edwards and th e Edwards logo are tradem arks of Ed wards Limited.Edwards and the Edward s logo a re trademarks of Edwards Limited. Installation 3.6.4 Connect to the t hermal snap-switche s CAUTION Ensure that you route the thermal snap -switch cable away from hot surfaces of the pu mp or o ther e quip ment. If you do not, the cable may be damaged. Connect the output of the warning thermal snap -switch to yo ur control equipment to prov ide an indication that the pump is too ho t. You must connect the outp ut of the shut-down ther mal snap-swi tch to the electrical-overl oad control-lo op of your contactor, so th at the contacto r will automati cally swi tch off the p ump if it is too hot: refer to Figure 3. The thermal sn ap-switches will reset (tha t is, close aga in) when t he pump cools d own to a pres et temperat ure (see Section 2.5 ). We theref ore recommend th at your contro l equipm ent incorporates a manual reset device so that the pump does not auto matically swit ch on again when it cools down. Use the following procedure to connect to th e thermal snap -switches. If you connect to the thermal snap-switches as described be low, the output from the therm al snap-switc hes will be normally clos ed and will open when the pump is too ho t. 1. R efe r to Figure 6 ( page 20 ). WARNING You must connect the sh ut-down thermal snap-switch so that the pump stops when the thermal snap-switch open s. If you do not, ther e may be a risk of fire or explosion. If you do not (and a fault which causes the sh ut-down ther mal snap-switch to open is not co rrected), the pump will automatically switch on again when it cools down. If you have started maintenance or fault finding on the pump, there will then be a risk of fire or explosion and injury to people. Page 19 Edwards and th e Edwards logo are tradem arks of Ed wards Limited. Installation A705-61-88 0 Issue K 3.7 Check the direction of rotation 1. R efe r to Figure 1. Undo and remove the four bolts w hich secure th e coupling cover (15) to the coupling housing, then remove the coupling cover. 2. R efe r to Figure 12. Look into the coupling housing (5) and watch the driv e hub (14), swi tch on the p ump for one or two seconds, then sw itch the pump off. 3. If the drive hub (14) does not rotate in the corr ect directio n (shown by an ar row on the pump-motor: Figure 1, item 18), the direction of rotation is incorrect. If the direction of rotation is incorrect: z Isolate the pump from the electrical supply.R efit the coupling cover (15) and secure with the four bolt s. T ighten the bolts to a torque between 3 and 5 Nm (2.2 and 3.7 lbf ft). 3.8 Fit a mechanical booster pump (optional) If you want to use a mechanica l booster pump with the GV pump, fit it now. Details of the con nection kits availabl e from Edwards are given in Section 7.4. Refer to the installation proc edures i n the instructi on manua l supplied wit h the connection kit. WARNING You must ensure that the direct ion of rotation of the pump is correct before you operate the pump. If you do not, and the pump direction of ro tation is incorrect, th e inlet pipel ine will be pressurised and may be damaged and there will be a risk of injury to people or explosion or fire. Edwards and the Edward s logo a re trademarks of Edwards Limited. Installation Figure 6 - Connect to the thermal snap-switches 1. Bolts (4 off) 2. Cover 3. Thermal snap-switch box 4. Four-core cable 5. Cable-gland 6. W arning wires 7. Spade terminals 8. W arning thermal snap-switch 9. Shut-down thermal snap-switch 10. Spade terminals 11. Shut-down wires Page 21 Edwards and th e Edwards logo are tradem arks of Ed wards Limited. Installation A705-61-88 0 Issue K 3.9 Connect the cooling-water supply Note: The following procedure assu mes that you use the GV pump with direct cooling, as supplied. If you want to use indirect cooling on the GV pump, insta ll the appropriate Indirect Coo ling Kit (see Section 7.4 ) and connect to the cooling-water supply as described in th e instruction manu al supplied with th e Kit. Take note of the following whe n you connect the coo ling-water suppl y and retu rn pipelines: z If you need to connect more than one GV pum p to th e water supply, you must co nnect them in parallel and not in series.Connect the c ooling-water supply as descr ibed below; yo u must use.You must connect nitro gen supplies to the gas sy stems if you will pump da ngerous gas es.A s supplied, the gas-ballas t system can deliver filtered atmospheric a ir to the pump gas-ballast inlet, so you d o not need to connect an air supply to the gas- ballast system.Us e the pro cedures in Section 3.10.2 and 3.10.3 to connect nitrogen supplies to the shaft-seals purge inlet and to the gas-ballas t system. Edwards and the Edward s logo a re trademarks of Edwards Limited. Installation 3.10.2 Connect the shaft-seals purge air or nitrogen supply CAUTION Your compressed air or nitro g en supply pressu re must comp ly with the requirements of Section 2.7. If it does not, the shaft-seals purge pipeline may become over-pressurised and the shaft-seals may fail. Note: Your compre ssed air or nitro gen gas supply must be clean and dry. We recommend th at you instal l suitable pres sure control dev ices, a pressu re gauge, and an au tomatically op erated isolatio n-valve in your compr essed air o r nitroge n supply conf igured so that: z The shaft-seals purge air or nitrogen supply is on whenever the pump is on.R emove the red blanking cap from the s haft-seals purge inlet (2 2). 2. R emov e the ? inch co mpression nu t and ferrule from the fit tings kit and fi t them finger -tight onto the shaft- seals purge inlet con nection (22). 3. Fit th e end of y our air or nit rogen supp ly pipeline to the shaf t-seals pur ge inlet c onnection (2 2), then tight en the nut to secure the pipeline in place. 3.10.3 Connect a nitrogen ga s-ballast supply (optional) Note: Ensure that the gas-ba llast nitrogen supply is clean and dry. Y o u r n i t r o g e n s u p p l y p i p e l i n e m u s t t e r m i n a t e i n a K F 1 6 f i t t i n g, t o e n a b l e y o u t o c o n n e c t i t t o t h e f l o w v a l v e. If required for your a pplication, yo u can connect a non-venting (to atmosphe re) nitrogen gas-ballast supp ly to the pump. You mu st connect a non-venting (to atmosphe re) nitrogen gas-ballast supply to the pump if you will pump dangerous gases. When you conne ct a nitrogen s upply to the g as-ballast s ystem, we re commend that you incorporat e a suitab le pressure gauge in th e nitrogen supply pipeline. Use the following procedure to connect a nitroge n supply to the gas-ballast system: 1. R efe r to Figure 7.